Aerial Bundled Cable, ABC Cable, Overhead Cable, ASTM, BS, Nfc, IEC, DIN Standard
|FOB Unit Price:||US $0.6 US $0.56|
|Purchase Qty. (Meters)||FOB Unit Price|
|Transport Package:||Standard Export Drum|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: abc
- Conductor Type: Stranded
- Conductor Material: Copper
- Material Shape: Round Wire
- Brand: Rne Da
- Cross Section: 10mm2-300mm2
- Cores: 1, 2, 3, 4, 5, 6
- Specification: IEC60502, IEC61089; NF C33-209; GB 12527-9
- HS Code: 85444921
- Type: Insulated
- Application: Power Transmission
- Insulation Material: XLPE
- Certification: ISO9001
- Rate Voltage: 600/1000V
- Insulated: XLPE or PE
- Trademark: RNE DA
- Origin: Hebei, China
IEC60502, IEC61089; NF C33-209; GB 12527-9; ASTM B231, ASTM B232, BS215; DIN48201, DIN48204.
We can also manufacture ABC cable according to customer's special requirements.
The cable as a new-type aerial cable is used for transmitting electric power overhead, extensively used in rebuilding of urban and forest region electrified wire netting. It improves the safety and reliance of electrified wire netting. To be used at cotages of 600V phase-to-phase or less and at conductor temperatures not to exceed 75ºC for polyethylene insulated conductors or 90ºC for cross-liked polyethylene(XLPE) insulated conductors.
Concentric strand aluminum wires as phase conductor; AAAC(all aluminum alloy conductors) or ACSR(aluminum conductor steel reinforced) as messenger (Neutral) core;Phase conductor is insulated by XLPE or HDPE or PVC.
It meets or exceeds the following specifications:
1). Aluminum Wire, 1350-H19 for Electrical Purposes.
2). Aluminum Conductors, Concentric-Lay-Stranded.
3). Aluminum Conductor, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR).
4). Concentric-Lay-Stranded 6201-T81 Conductors.
5). Compressed Round Stranded Aluminum Conductors Using Single Input Wire.
It meets or exceeds all applicable requirements of ANSI/ICEA S-76-474
4 Type of XLPE(PE) insulated ABC cable (service drop)
XLPE(PE) insulate cable (service drop)covers mainly three types:
Duplex Service Drop
Triplex Service Drop
Quadplex Service Drop
The basic construction is as follows:
3 power cores consisting of standard aluminum conductors, insulated with XLPE insulation
+ One sheath lighting aluminum conductor with XLPE insulation(optional)
+ One messenger Al-alloy conductor (bare or covered)
The messenger conductor can be of galvanized steel wire also.
The purpose of messenger wire is:
A) It acts as load bearing wire.
B) It acts as earth or neutral conductor.