For Medium Cabl, we have UL certificate, TUV and KEMA type test report.Advantages of Hebei Huatong Cables Group:Top ten cable manufacturer in ChinaLargest manufacturer&exporter of UL listed cables in China
Annual export volume exceed USD300million
UL, CUL, CSA, TUV, KEMA, CE, BV, PSB, SABS, LLOYD'S, GL, NK, KR, ABS certificates
CNAS approved lab!
xlpe 11kv power cable price:1 Application:It is used to transmit and distribute power in power transmission and distribution system of 35kV or lower. It is generally applied to the fields including power, construction, mines, metallurgy, petrochemical industry and communication in complete replace of oil immersed paper insulated power cable and in partial replace of PVC insulated power cable. Power cables for power networks, underground, outdoors and in cable ducting 2 ConstructionStandards: BS6622, BS EN/IEC 60228,IEC60502.2Conductor: Class 2 stranded plain copper conductor to BS EN 60228:2005 (previously BS6360)Conductor screen: Semi-conducting materialInsulation: XLPE (Cross-Linked Polyethylene) Type GP8 to BS7655Insulation Screen: Semi-conducting materialMetallic Screen: Individual and overall copper tape screen to BS6622Filler: PET (Polyethylene Terephthalate) fibresSeparator: Binding tapeBedding: PVC (Polyvinyl Chloride) Type TM1 to BS7655Armoring:Single Core: Aluminum Wire Armored (AWA)MultiCore: Steel Wire Armored (SWA)Sheath: PVC (Polyvinyl Chloride) Type TM1 to BS7655Color: Red or Black 3 Using features:1.Rated voltage: Uo/U:3.6/6kV, 6/10kV(11kV), 12/20kV(24kV), 19/33kV, 26/35kV(35kV).2. No. of core: Single core or three cores.3. The highest allowed operating temperature of conductor for long-term working is 90oC. In short-circuit (Max. long-term is no more than 5 seconds). The highest temperature for conductor is no more than 250ºC.4. D.C. resistance of the conductor complies with the stipulations of 3.6/6kV, 6/10kV(11kV), 12/20kV(24kV), 19/33kV, 26/35kV(35kV).5. The environment temperature should be no lower than 0oC when lay. Otherwise it should be preheated.6. The cable is laid without horizontal drop limit.7. Working Frequency Voltage Test: 3.5Uo/5min without puncture.8. Partial Discharge Test: The discharge volume should be no more than 10pC under 1.73Uo for the cable.
Company Introduction:HeBei huatong wires&cables Group Co.,ltd.It was established in 1993, we are JV with Furukawa(Japanese company) for rubber serious cables and JV with Riken(Japanese company) for elevator cables. Besides these,our submersible oil pump cable and shipboard cable are very influential in domestic, and, the traditional cables are also produced such as PVC powercables, XLPE power cables, ABC cables, wires, control cables, screened cables,communication cables, conductors.We areOEM for many USA, Europen, Australia cable company,70% of our products are exported, most customers are from developed countries. We got ISO,UL,TUV,KEMA,CE and many other certifications.Contact Information: